What is the recommended fire area when designing and placing equipment in a facility? In another word, when planning the general layout of a facility, what should be considered?
Confirm to permanently remove your answer!
Per API RP 521, if the equipment is located in an area where type and volume of the inventory and drainage system design is such that a sizable fire might occur:
The horizontal extent of fire zone should be a 65 ft diameter circle from a potential source of fire. A shorter fire zone could be assumed if equipment is segregated by firewalls or by a curbed area capable of containing or restricting the exposure to the spilled inventory.
Assume that all piping and equipment up to 25 ft above deck, ground, or any other fire-supporting surface is exposed to fire.
For air coolers with tubes located higher than 25 ft above grade or other surface at which a major fire could be sustained, the extent of fire should be as follows: