Can someone recommend the design and fabrication requirements of expansion joints intended for use in low pressure air and flue gas service associated with fired heaters, boilers, and other fired equipment?
Confirm to permanently remove your answer!
You should specify the followings when request for cost estimate:
The design life should be the greater of 10 times the anticipated number of cycles in 20 years, or 1000 cycles.
The design pressure should be the greater of:
The design temperature should be 50°F (28°C) above the maximum short duration temperature.
All expansion joints should have an external shroud to protect them from damage.
An internal baffle should be provided to protect the flexible element from debris in the air or gas stream.
Ceramic fiber insulation, encased in a ceramic fiber cloth bag, should be installed in the void area between the metal bellows or fabric belt and the internal sleeve.
Metal temperature of expansion joint parts in contact with the flue gas should be maintained above the acid dewpoint.
Attachment of fabric belts should be such that they can be replaced without dismantling the joint or removing it from the ducting.
Slip joints may be used where motion is <1 in. (25 mm) and will occur in one plane only.